AHU Fan Drive Replacement, The Royal Marsden Hospital, Chelsea
At the Royal Marsden Hospital in Chelsea, the existing critical fan drive motors were failing. The client also needed to increase air volume due to changes in use in the area served by this air handling unit.
ECEX surveyed, specified and installed a new Comefri backward curved direct drive fan complete with 11kw fan motor & inverter.
Thanks to the upgrade, the client benefited from increased volume, reduced maintenance time and cost due to elimination of belt drive, lower energy consumption and life cycle costs. The new drive fan also allows for rapid change out in event of future failure (just 8 bolts and quick-release commando connection).
For more information about our AHU refurbishment services, for hospitals and other commercial buildings, click here.